This is an old revision of the document!
Author: Barry Gordon
CommandFusion Products: iViewer 4
This material may not be reproduced or reused elsewhere without the express written permission of Barry Gordon.
The purpose of this system is to control all of the Home Automation attributes of my home and to display their current state at any time.
The house was designed by my late wife, Jill and myself circa 1997. We moved in on my birthday October 1, 1998. The house is a single story open floor plan design with about 3800 sq. ft. of space under air, with an additional 1500 sq. ft. (the garage) not under air. Ceilings in the house are 10 feet, except in the Great Room where they are 12 and 13 feet. The exterior walls are concrete block. We had the builder do a full 2×4 interior inside the concrete block. This makes the walls very thick providing a pleasing architectural look to the window openings. In addition it makes it easy to mount pictures; Jill was a needlepoint artist. The roof is concrete tile.
The house is logically divided into zones:
The electrical system for the house is 300 amp service split to two 150 amp service panels. One panel has a backup generator sized to run that complete panel and propane driven from a 500 gallon underground storage tank which also supplies the gas needs of the house. The system is ready for a second generator, but I have not yet seen the requirement. Special care was taken to ensure a proper system ground (8' x 1” copper pipe driven into the ground at the service entrance). Every box which takes switches, and every ceiling junction box have neutrals to allow for the operation of sophisticated electronic switches (X10, Insteon) without problems.
The view of the house from the street it resides on (a little old, landscaping has changed):
The floor plan (not to scale) for the house roughly aligned with the above picture:
Each zone of the house, except the Lanai and the Utility zone, has a wall mounted iPad. The guest wing has two, one in the guest bedroom and one in the office. There are announcement speakers mounted in the ceilings of all the major rooms.
The main zone, the great room, has three zones of music, each with its own volume control, but all playing the same source. After all, it is just a large open space. The master bedroom has an audiophile quality “stereo only” audio system, while the theater has a full 7.1 audiophile quality sound system to match its 133” HD projection system.
All software (code, data, music, video) is maintained on a 16 TB server which is expandable to 44 TB. Music is served by the “Squeeze Server” system (aka LMS, aka Slim System) while video (movies) are handled by a system I developed specifically for my theater. If I were to do it today I would just use XBMC.
The wall mounted iPads are actually in the wall using a docking system that is slightly thinner than standard wallboard. This means that iPad placement is independent of stud locations and makes for a very high WAF. The iPads can be reloaded and restarted on command from a central point. They are constantly being charged, and revert to a black screen with the backlight off when not used. They become active on a double tap, or when commanded to display a callerID or similar message by the Home Automation system.
The Home Automation system is “Homeseer” and runs on a dedicated rack mounted 2U server. The rack is in the utility closet which has its own HVAC system so it is never heated in the winter whereas the main living areas might be. The lighting sub-system is being migrated from X10 to Insteon under the control of a Universal Devices ISY994i. The ISY994i is integrated with Homeseer so that all status can be collected at a single point. The house has two zones of Air Conditioning controlled by the ISY994, and Homeseer directly monitors the security system.
The design of the Home Automation system is based upon independently operating subsystems (Security, HVAC, Lighting, etc.) all coordinated by a single overseeing entity - Homeseer. The system will operate completely without Homeseer or the ISY994 or the iPads, just not as conveniently.
All of the electronics (PC based) rides on a single Local Area Network (LAN) with high speed access (60 mb/s) to the Internet. Phone traffic is Internet based (VOIP). The network is 100 mb/sec using only twisted pair (Cat 5e). The systems are very reliable with up times measured in years, not counting planned off times for maintenance and upgrades.
All the PC's in the house run Windows 7 and can be remotely controlled from the PC in my office which is my development system. It is a very fast system that I designed and built from scratch. I do that with most of the PC's in the house. This system has 15,000 rpm SCSI drives, 6 GB of very fast memory and a high speed 4 core processor. The monitor has a screen size of 28” and runs at 1920×1200.
The entire server rack, all of the networking equipment and all of the A/V equipment is powered with a 1.5 KVA backup UPS. The backup generator will start in about 20 seconds after a power outage and powers all of the UPS protected components before the UPS batteries cause them to go offline. Because of the UPS, the switching to and from the generator is seamless to the installed electronics.
The local ISP (cable TV and Internet) feeds into a CATV signal splitter (1:2). One output goes to the TV signal distribution system (1:8) and the other to a Motorola cable modem. The cable modem has its own internal battery backup. All the equipment associated with Ethernet, TV and telephone signal distribution is feed off Panel A, but is not UPS protected. I have plans to change this so the “Head End” signal distribution system is powered off the Utility closet UPS.
The output of the cable modem is fed into a Linksys router which has an internal 4 port Ethernet switch and handles two channels of Voice over IP (VOIP). Only two of the Ethernet ports are used, each of them feeding a 16 port Ethernet switch for a total distribution system of 32 Ethernet lines.
Three lines from one of the Ethernet switches go to POE voltage inserters and then to the three ceiling mounted WAPs. The remaining Ethernet circuits go to wall jacks in the various rooms and the outdoor pool area. Several of the rooms (Utility closet, Master Bedroom, Theater, and the Office) have a second 8 port Ethernet switch for local signal distribution.
The Ethernet wiring is all UTP CAT 5e and runs at 100 mbps. No run is greater than 100 feet, and no path between any two devices consist of more than three hops. There are WAP's located in the Theater, the Master Bedroom and the Great Room ceilings.
The network runs very lightly loaded (2-5%) unless I am playing music or watching a movie. I have not yet had a need to run two movies at the same time as I live alone, however I suspect it will probably work. Download speed from the WWW averages about 60 mbps.
The house also has a cell phone repeater system. The outdoor antenna of the repeater is aimed at the cell tower that services my geographic area on a direct line of sight. This was done because the house construction is of concrete block with a large amount of rebar. This made cell phone reception in the house very poor.
The remainder of this document will concentrate on the system I developed for the wall mounted iPads. The fact they are wall mounted is not germane to the system design.
My philosophy regarding home automation has evolved over the years. Things change, new capabilities come about, I change.
First and foremost I want important things e.g. Security, HVAC, Lighting control) to work even when computers fail. Not if, but when. The key characteristic of my HA system is that major subsystems (HVAC, Security, etc) will operate with no computers in the loop. This is also important from a home resale factor. The next owner, and there will be one, may not have the same computer orientation that I do.
The HA system has one major “Brain” and that is the Homeseer HA software product. Information about all subsystems is constantly sent to Homeseer from sub-controllers (ISY994 for Insteon devices, Autelis controller for the Pool/SPA, iPads, etc.).
Dynamic scheduling, i.e. the scheduling of events based upon changing status, or by request from a user via an iPad; is handled by Homeseer, with some simple fixed schedules (e.g. landscape lights on at sunset + 30 minutes) handled by the ISY994.
The iPad is used as the primary user interface to all HA functionality. You can change the state of a light for example; from an iPad, from the ISY994, from Homeseer, and most importantly from the switch that directly controls that light. All lighting switches are computers and they will fail at some time. Such failures are single point in nature, of minor operational consequence, and no different than the light bulb burning out. The systems must be self restarting and self healing to the greatest degree possible. All major computers are setup to automatically restart after a power loss. Power loss to the electronic systems in my home is extremely rare due to the use of UPS and a standby generator. I live in the state of FL in the US. The central region (where I am) of FL is the second most prevalent location for Air-to-Ground lightning strikes in the world. Momentary power outages and voltage fluctuations are the norm.
I have never had to replace a computer or other piece of electronics gear due to a power related event, and there is a lot of electronics in my home, probably way to much.
There are several display pages three of which are special. The first page, the splash page, is only seen on a boot of the system while all images are cached into the memory of the iPad, and the configuration tables are processed.
The second special page is the home page and all other pages revert to this page after a period of inactivity. When the home page has been inactive for a configured length of time, it reverts to an all black screen, and after several minutes of that page being displayed the iPad backlight is turned off. This is done since a wall mounted iPad is quite bright even with an all black screen at minimum brightness. Too bright for a bedroom at night IMHO.
The final special page is the Caller ID page. This page is shown for 15 seconds when a phone call is received. It displays the originating phone number and the caller's name. At the same time Homeseer is announcing the call giving an alias name, if available, based upon the originating telephone number.
The remaining pages with the exception of the first page all follow an identical layout. The left and right hand sides contain buttons to move between the various functions. Each function has a dedicated page whose central area contains the controls and displays for that function.
I keep my project folders, the root folder and directory tree that make up a project, in a master folder on my web server. This folder is not accessible external to my LAN and is where all my iPads go to load their systems.
Each project has one JS module (I generally name it “Main”) that is written in “pure JS” and not as a large object. There is also a second “pure JS” module that holds functions common to all the other modules. This causes things in those modules which are externally available to be named directly without the need of a prefix representing the module itself. The Main module contains the CF.userMain function along with event handlers for page flips, Clock and Timing (called once per second), and preloading completion. The userMain function sets up “watches” for the major events.
The subroutine module contains many common library routines that I have found useful over the years. For example there is a function called uPack which takes a string argument, and returns the same string with all spaces removed and in uppercase. Very useful (and forgiving) when doing text compares. Most library functions are simple one liners, but some are more complex e.g. showHEX which displays any text string as a sequence of hex characters. This is very handy for viewing communications messages; showCOM shows a string with all formatting codes (Carriage return, tab, Line feed, space) explicitly visible using the standard ASCII mnemonics for the control codes. Another key function in the Subroutines module is the Dialog Function which handles popup displays for special notices such as troubles and errors.
All other modules (I call them the Work modules) are written as a single object encapsulating all the functions and data elements used by that module. This means that all functions and data elements defined in that module need to be referenced using the module prefix as the object name. For example, the Autelis Pool Control functions and key variables are contained in an object variable named PL, while the HVAC functionality is contained in an object variable named HV. [Note: I generally use two or three capital letters to name the object]. Ergo to access the Autelis module's initialization function one would write PL.initialize(a, b). This technique, which is recommended by the CF team, allows each module to have the same functions with no naming conflicts. Following the modules encompassing object definition a single line of code exists which is used by CF to instantiate the module and call its setup function if required.
The work modules supply supporting code to one or several pages. They have certain functions that I generally provide in every module with similar operational characteristics:
|setup:||Called by CF when the module is loaded.|
|initialize:||Initializes the module. It is normally called when a Page that uses this module is loaded (page flip event).|
|feedback:||The function that handles feedback from a system that is capable of two way communications. I generally code the feedback regex associated with an external device as (^*) which allows any string of characters and is equivalent I am told to (*) or (.). This presents to the modules feedback function the text received from the device up to that point in time. It should be noted that when dealing with RS232 and interface devices such as Global Cache units or the Xeta server (A single port TCP/IP to RS232 interface) a message may not arrive in a single packet. If the message protocol does not use a terminating sequence then code must be used to ascertain when the full message has been received and to validate its content.|
|actions:||The function that handles user actions such as button presses.|
|timeout:||Called when a timer associated with a message transmission times out waiting for a reply (feedback).|
|reset:||Called when the communications system needs to be reset to start looking for another reply, normally after a timeout or error.|
|send:||The function to send a command, or possibly resend, a command to an external device. The send function is responsible for enveloping the message in any necessary control characters and starting the transmission timer. In some systems it is possible to use a “sendQueue” to schedule many commands. A command will only be sent after the prior command has returned a reply.|
When dealing with an external system e.g. an iTach, a GC-100xx, A PC handling a specific capability in my home, or the ISY994i; I generally handle the code in a fairly uniform manner.
TCP system I did not write and only handle one connection at a time:
I setup the control system to be always on in the guiDesigner. As soon as I initialize the system I use CF.setSystemProperties to disable the system so it does not attempt to make a connection. I then enable and disable the connection as needed. I enable it when I am ready to send, and disable it after I receive feedback to the transmission.
If the transmission times out waiting for feedback, I reset the system (disable it) and resend the message. I will do this up to 5 times before declaring the system down.
If I am using a queue to drive the system I put items into the queue I want sent then start a send function which transmits the earliest item in the queue (FIFO operation). I pull the next item from the queue when feedback has been received and processed. This provides perfect timing for things such as IR macro sequences if the IR pattern has the proper final off time.
TCP systems using a server I wrote that handles multiple connections.
The system is setup as always on in guiDesigner and left enabled when I initialize the system. This causes iViewer to connect to that system and keep trying to do that periodically until successful. When successful we have what is known as an active session since I do not disconnect it. If the external system fails, iViewer will continuously attempt to reconnect.
Transmissions to the system are generally Queue based with an interesting caveat. I optionally include as a prefix in the transmission the name of the feedback function which is to process the reply. The server sends the feedback with this prefix as a prefix in the feedback message. This allows me to decide based on the feedback received, what process will handle the message with almost no effort.
TCP systems which I have no Control over.
I just obey the protocol that the system requires.
I know that the CF staff have made recent improvements in the handling of TCP systems and getting feedback. I need to update (simplify) my code to use their efforts.
Each module has debugging built in. The debugging aids consist of variables to control the level of debugging and when things will be placed into the CF.log file if debugging has been turned on. The production systems (wall mounted iPads) run with debugging turned off. The highest level debugging variable in each module is named trace. Almost every function has as its first line:
if(XX.trace) CF.log("The XX.nameOfFunction function has started with inputs= . . .");
This provides a simple flow trace when things do not work correctly after a change.
The system maintains a set of activity log files containing the most recent 50 log entries relating to a specific functionality, e.g. the ISY994. These log entries are not the same as those sent to CF.log for debugging, but document the progress of a specific application functionality as it is running. Significant events are logged as well as warning and error conditions. All asynchronous inputs from either Homeseer or the ISY994 are also logged here. This log can be displayed from a button present on most pages. The log display page allows for the selection of which particular log is to be displayed.
This a free text editor that I use as my standard editor. It understands the difference between PC and Unix line endings. It provides line numbers. It has a list of all the ASCII characters and their decimal indices.
A free utility that compares two files flagging all discrepancies with simple commands to correct or remove the discrepancies.
Configuration assets include: Interface definitions to external systems.
iViewer will not cache and guiDesigner will not export into zip files any resource that is not explicitly referenced in the guiDesigner XML output, the “gui file”. For that reason all configuration data is encoded into an object named “CFG” in the module “Configuration.js” which is referenced in the project script manager and therefore loaded. The CFG object contains sub objects with the configuration data for a logical entity e.g. a Rooms, Scenes, Interface connectivity, IR files, station (FM, Sirius) lists, and TV channel lists.
At startup after the completion of preloading as signaled by the firing of the preloadCompletionEvent, the system contacts Homeseer and the ISY 994 requesting the current status of every device that they directly control (X10 based devices, the Security system, Insteon device, etc..).
The configuration tables for all devices and systems (e.g. the pool system) are updated with the current state by recording: on/off state, brightness (0-255) if applicable, and a text string if applicable (e.g. standby battery voltage).
Homeseer will dynamically transmit status of devices under its control using a UDP broadcast message. [Note: the Homeseer status messages are sequence numbered and each message is sent N times (N=2) with the same sequence number. This reasonably handles the fact that UDP is not a guaranteed delivery protocol but rather a best effort protocol].
For the ISY994i, a message is sent to turn on subscriptions which cause the ISY994i to send to the iPads any and all status changes for every device it is cognizant of.
When a status message comes in the internal configuration tables are obviously updated. Most entries for a device configuration tables have a “display” sub object.
The display object has several sub objects which are used to drive the information on pages to be updated. The updates to the page displays take place whether they are visible or not. The graphics or text being updated may be in lists and may appear on different pages with the same or different join numbers. The display sub objects are as follows:
|Title:||Sets the text for a title string. Sets the text for the display graphic which might be in a list.|
|Icon:||Sets an image to one of two images based upon on/off state|
|Opacity:||Sets an images opacity between 1 and 0 based upon brightness|
|Slider:||Sets the position of a designated slider based upon brightness|
|Text:||Sets a text string based upon the current brightness with optional prefix/suffix|
|String:||Similar to Text, but uses the string returned by feedback or an asynchronous input|
[Note: for Opacity there are normally two icons at the same position on the page or in a list. The bottom icon is the “Off” icon to be visible when brightness is 0. The top icon is the “On” icon whose opacity is changed based upon the current brightness. At full brightness its opacity is set so it is opaque, at 0 brightness its opacity is set to be transparent. With the proper choice of Icons, this can be a very impressive display].
The remainder of the document will discuss the various pages that make up the iPad graphics. Some pages have multiple subpages and I will provide examples showing the page in various states.
The Home page or Idle page is the first page transferred to when the system has finished its initial setup, or when a page has “timed out”. Each page is timed when it is displayed. The timer is reset on any action to that page so it effectively determines the page's idle state. The Home page looks as follows:
The weather display is updated every hour by an external system which is queried when this page is loaded to be displayed. Each of the black buttons will transfer to a page that displays the state of that function and has the necessary buttons for control.
There are two buttons that do not operate that way; the button for the SqueezePad music system and the button for Movie Showtimes. These two buttons use a URL Schema to load either the SqueezePad app. or the IMDB app. iViewer then will be in the background still running since it is run in multitask mode. Exiting those apps just require a single click to bring iViewer and the system back into view; or if the version of IOS is recent a 4 finger swipe will go back to the prior app in the active multitasking list. These buttons use a Brass coloration to differentiate them.
This is the weather detail page. The top portion of the page is the current weather as recorded at the stated time. The graphics all change based upon the weather conditions and the background changes from blue to gray at night (after sunset) and back to blue at sunrise.
The bottom portion of the page is a scrolling list that holds a week's forecast showing both day and night conditions. There are no controls on this page other than those on the right and left for changing the page being displayed. Obviously the ability to scroll the forecast list exists.
This page displays all of the status received from the Autelis control system that monitors and controls the pool and SPA. The status is dynamically updated as things change. The various on/off buttons will control the functions they are titled to. The SPA may be scheduled for turn on by adjusting the values in The “Set SPA Turn On” region. Homeseer is used to handle the scheduling of a SPA turn on event.
The Autelis control will maintain only a single IP connection at a time. The logic for sending it commands involves (1) connecting, (2) sending the command, (3) waiting for the feedback response and then (4) disconnecting. If a connection cannot be made (another iPad is connected) it is re-tried at 500 millisecond intervals until successful or a maximum retry count has been exceeded. If the maximum retry count is exceeded a dialog is place onto the screen to inform the user of the issue. Note by CommandFusion: You could get around the issue of a single connection by using a CommandFusion LAN Bridge as a multiplexer.
The Autelis Control will send UDP messages for each change of state for any of the pool devices. It sends each message twice as a sequence numbered UDP broadcast to all hosts on the network.
This page is similar in concept to the Pool/SPA page but handles the two zones of Air Conditioning in my home. The system uses Insteon thermostats and the associated control logic. Each Thermostat talks to the ISY994. The use of the controls on the page should be obvious. The system updates dynamically whether the page is visible or not.
Displaying the page merely displays the current values since the joins were updated as the components they represent changed and asynchronous (unsolicited) feedback was received.
The lighting control page handles all lighting for the house. When flipped to, it will initially show the list for the room the iPad is in. Lighting status is continuously updated whether this page is visible or not. The lower part of the list is normally not visible. It is made visible by touching the title of a light in the list. The list then rolls up to expose the slider. If the entry in the list has a percentage to the right of the bulb icon, then there is a slider associated with that light and the list may be rolled up to expose the slider.
All lighting is controlled by the ISY 994, as are all Insteon devices. The ISY994 can handle 10 simultaneous clients (in my case a client is an iPad), and a relatively unlimited number of devices. Each iPad “Subscribes” to the Insteon during startup, after requesting the ISY configuration and the status of all the devices under ISY994 control.
This page is very similar to the Lighting control page. When this snapshot was taken the Cable box wall receptacle was powered and the Hot water circulator was operating. All other devices were off/closed. The cable STB in the kitchen is out of reach so to “reboot it” was a pain in the butt. It no longer is.
The hot water circulator is a small pump to circulate hot water to every fixture in the house. The house is large so waiting for hot water to arrive at a shower can be a little annoying. The circulator only runs when the house is disarmed and between 7AM and 11PM. If however you walk into a bathroom and turn on the lights, then the circulator immediately starts and runs for one hour. The devices under the control of the ISY994 include Thermostats, Lighting switches, Relays to control outlets etc.
The above is the call status page showing calls received. The actual callerID page is bright with a telephone as the background, using large type so it can be read from across the room. The Caller ID page shows who called, and the callers number. The CallerID page is displayed for 15 seconds and then the system reverts to the prior page, generally the black screen.
Homeseer handles the incoming call using a caller ID device which sends it the Caller ID information over a serial link. Homeseer looks up the phone number in a special list to see if it is a known number and if so changes the name displayed to a more readable piece of text. Homeseer announces the call over the house's announcement system (a ceiling speaker in each major room) stating the phone number and the name.
The caller ID message is also broadcast to the Theater control PC. That PC has a list of callers by number for which it will pause the theater (Movie, TV show, whatever is playing) so that the call can be answered, and displays the incoming call on its control screen. When I am finished with the call in the Theater, I just touch the “Play” button on the theater's remote system (Philips Pronto PRO 9800).
At one time the DOW was displayed but that changed when the owners of the DOW index stopped supplying the feed. The button labeled “Market Dash” will bring up the Market Dash app using its URL Schema. Unfortunately they do not supply a return option in their Schema. If the IOS is recent enough, then a 4-finger swipe can be used to bring back iViewer.
This app has all of the DOW information plus history and trend data.
The current status of any stock can be queried using the “By Symbol” button after entering the symbol in the text filed provided. The portfolio configuration is maintained by Homeseer from a text file which is easily changed with a text editor.